Download 5.8 Mb.
All rights reserved.
The information in this document is subject to change without notice.
Thank you for purchasing this series UPS.
This series UPS is an intelligent, three phase in Three phase out, high frequency online UPS designed by our R&D team who is with years of designing experiences on UPS. With excellent electrical performance, perfect intelligent monitoring and network functions, smart appearance, complying with EMC and safety standards, The UPS meets the world’s advanced level.
Read this manual carefully before installation
This manual provides technical support to the operator of the equipment.
Important safety instructions – Save these instructions
There exists dangerous voltage and high temperature inside the UPS. During the installation, operation and maintenance, please abide the local safety instructions and relative laws, otherwise it will result in personnel injury or equipment damage. Safety instructions in this manual act as a supplementary for the local safety instructions. Our company will not assume the liability that caused by disobeying safety instructions.
1.1 Safety notes
Even no connection with utility power, 220/230/240VAC voltage may still exist at UPS outlet!
For the sake of human being safety, please well earth the UPS before starting it.
3．Don’t open or damage battery, for the liquid spilled from the battery is strongly poisonous and do harmful to body!
4．Please avoid short circuit between anode and cathode of battery, otherwise, it will cause spark or fire!
5．Don’t disassemble the UPS cover, or there may be an electric shock!
6．Check if there exists high voltage before touching the battery
7．Working environment and storage way will affect the lifetime and reliability of the UPS. Avoid the UPS from working under following environment for long time
◆ Area where the humidity and temperature is out of the specified range (temperature 0 to 40℃, relative humidity 5%-95%)
◆ Direct sunlight or location nearby heat
◆ Vibration Area with possibility to get the UPS crashed.
◆ Area with erosive gas, flammable gas, excessive dust, etc
8．Keep ventilations in good conditions otherwise the components inside the UPS will be over-heated which may affect the life of the UPS.
1.2 Symbols used in this guide
Risk of electric shock
Read this information to avoid equipment damage
Our UPS is a kind of three-in- three -out high frequency online UPS, it provides three specifications: The 150~600kVA. The products are modularized and adopt the N+X redundancy. It can flexibly increase the number of the UPS modules according to the load capacity which is convenient for flexible allocation and gradually investment.
The UPS can solve most of the power supply problems, such as blackout, over-voltage, under-voltage, voltage sudden drop, oscillating of decreasing extent, high voltage pulse, voltage fluctuation, surge, inrush current, harmonic distortion (THD), noise interference, frequency fluctuation, etc..
This UPS can be applied to different applications from computer device, automatic equipment, communication system to industry equipment
2.2 Functions and Features
◆19-inch standard cabinet
1.2-meter, 1.6-meter and 2-meter high cabinets are provided according to the user’s requirement.
◆High power-density design
The height of the single module is 3U.
◆N+X parallel redundancy
This series UPS adopts N+X parallel redundancy design, user can set different redundancy according to the importance of the load. While the redundancy modules are set more than two, the availability of UPS system will achieve 99.999%, which may satisfy the required reliability of the critical load connected. Through LCD display setting, you may configure the required quantity of the redundancy unit. When the load connected is over the number of the redundancy, the UPS will alert right away. The design of the MTBF (Meantime before Failure) is up to 250,000 hours.
This series can set the number of redundancy modules. When the load exceeds the redundancy setting, the UPS can still work normally and simultaneously send out corresponding warning as long as the load doesn’t exceed the total capacity of modules.
◆Parallel redundant control system
◆Optimizing distributed convergence for the cabinet
◆Automatic charge current adjustment according to battery capacity connected.
◆3-Stage Intelligent charging
◆Touch-screen Super-large LCD display
◆Remote monitoring via SNMP
◆Optional Accessories available such as Isolation transformer, distribution Panel, SNMP Card,
Relay Contact Board, etc...
◆Equip with Maintenance Bypass Switch for easy maintenance purpose.
◆Superior MTTR (Meantime to repair) & Short shutdown time in maintenance
◆Centralized monitoring module is also available
◆EPO and REPO function
2.3 Model description
This document describes the following UPS models:
The models provide 3 configurations: 50 kVA, 100 kVA and 150 kVA.
The models provide 5 configurations: 50 kVA, 100 kVA, 150 kVA, 200 kVA and 250 kVA.
The models provide 4 configurations: 50 kVA, 100 kVA, 150 kVA and 200 kVA
The models provide 6 configurations: 50 kVA, 100 kVA, 150 kVA, 200 kVA, 250 kVA
and 300 kVA.
The models provide 8 configurations: 50 kVA, 100 kVA, 150 kVA, 200 kVA, 250 kVA, 300 kVA,
350 kVA and 400 kVA.
The models provide 10 configurations: 50 kVA, 100 kVA, 150 kVA, 200 kVA, 250 kVA,
300 kVA, 350 kVA, 400 kVA, 450 kVA and 400 kVA.
The models provide 12 configurations: 50 kVA, 100 kVA, 150 kVA, 200 kVA, 250 kVA,
300 kVA, 350 kVA, 400 kVA, 450 kVA, 500 kVA, 550 kVA and 400 kVA.
◆ 150kVA supports cable routing from the bottom.
◆ 250kVA supports cable routing from the bottom.
◆ 200kVA supports cable routing from the top and can support cable routing
◆ 300kVA supports cable routing from the top and can support cable routing
from the bottom if a cable entry cabinet is configured.
◆ 400kVA standard cabinet supports cable routing from the top.
◆ 400kVA full configuration cabinet supports cable routing from the bottom and top.
◆ 500kVA supports cable routing from the bottom and top.
◆ 600kVA supports cable routing from the bottom and top.
* Standard configuration : cabinet only with maintenance bypass switch
* Full configuration : cabinet with mains, bypass, maintenance and output switch
3.1 Unpack checking
1. Don’t lean the UPS when moving it out from the packaging
2. Check the appearance to see if the UPS is damaged or not during the transportation, do not switch on the UPS if any damage found. Please contact the dealer right away.
3. Check the accessories according to the packing list and contact the dealer in case of missing parts.
3.2 The appearance of the product